Tags: Climate control | Whitepaper
4 February 2016,
Successful incubation in hot, humid climates poses a number of challenges for the hatchery, one of which is achieving sufficient weight loss at transfer to deliver high hatchability and optimal chick quality.
For example, a moderately hot and humid climate of 30°C with 75%RH at sea level contains approx. 20g H2O/kg air. If we assume a setter climate of 37.5°C and, with the aim of optimising weight loss from fresh egg weight at transfer of 12%, we choose a set point of 50% RH, the air in the setter will contain approx. 21g H2O/kg.
With the setter’s air valves closed, evaporating water from the eggs will increase both the absolute (gH2O/kg air) and relative (RH%) humidity of air in the setter. This limits evaporation from the eggs, making it impossible to achieve 12% weight loss.
By ventilating the incubator with fresh air, evaporating water from the eggs can be removed via the outlet, while maintaining an optimal incubation climate. However, using the example above, each kilogram of air entering the incubator can extract only 21g – 20g = 1 gram of water. This requires a lot of ventilation, starting early in incubation, to allow the hatching eggs to lose sufficient weight.
Adopting a non-linear weight loss profile that starts incubation with high RH% (by sealing the setter for several days), then compensating for low weight loss by applying a low RH% (ie. less than 45%) during the second half of incubation, is not feasible in hot, humid conditions. Such low levels of RH% simply cannot be achieved, even when air valves are 100% open. This is because when RH% set point inside the setter is, for example, 45%RH, the inlet air (30°C / 75%RH=20g H2O/kg) already contains more water (37.5 °C/45 %RH = approx. 18g H20/kg.). In this scenario, a linear weight loss profile based on a constant RH% of approx. 50% is much easier to achieve.
It is possible, at least partially, to overcome these challenges and minimize the need for high ventilation rates early in incubation, by optimizing the temperature and relative humidity of inlet air using an Air Handling Unit. Outside air of 30°C / 75%RH can be climatized to, for example, 25°C / 60%RH, which significantly reduces the water content of the air from 20g H2O/kg to approx. 12g H2O/kg. Again using the above example, each kilogram of air entering the incubator now has the capacity to extract 21 – 12 = 9 gram of water.
There is a downside to treating hot, humid outside air in this way. It requires energy, both for the cooling needed for dehumidification and also to subsequently re-heat the air to a recommended inlet temperature of 25°C (+/- 2 °C). A heat recovery system, which uses energy present in the return water from the incubator’s cooling circuit, is an effective way to reduce heating costs. Additional, albeit reduced, energy costs will still increase the cost price of the day-old-chick – but this does give the hatchery manager an additional tool for better controlling hatchability and chick quality in a challenging, hot and humid climate.